Questo sito utilizza cookie di profilazione (propri e di terze parti) per ottimizzare la tua esperienza online e per inviarti pubblicità in linea con le tue preferenze. Continuando a utilizzare questo sito senza modificare le tue preferenze acconsenti all’uso dei cookie. Se vuoi saperne di più o negare il consenso a tutti o ad alcuni cookie clicca qui>
The website that you are visiting also provides Arabian language. Do you wish to switch language version?
يوفر موقع الويب الذي تزوره المحتوى باللغة العربية أيضًا. هل ترغب في تبديل إصدار اللغة؟
The website that you are visiting also provides Russia language Do you wish to switch language version?
Данный сайт есть в английской версии. Желаете ли Вы перейти на английскую версию?
From the NetEcol, we found there is an Alarm of Skylight. Hence , we try to check on the IDS2000 room and found that one of the skylight is opening there.
Skylight Ceiling Controller Output Status 24 Open
1.) Use Multi Meter to measure the Port on the Sky Light Controller which is connected to Sky Light. It should be 12V. There should be 4 Connection to the Sky Light ( 4 Unit ). If you found 1 of the Connection did not give output of 12 Volt, you can change it to others port. Positive or negative connection doesn’t matter for this connection. Any Group or any Port also doesn’t not matter for the connection.
2.) Measurement of the Cable on the Sky Light before it connected to the Magnetic Controller.It should give 12V output also. If it doesn’t, we will check the cabling if there is any broken / break in between.
3.) If the Voltage is Normal from the Skylight Controller which give 12Volt output, We will take a measurement on the Magnetic Controller.The measurement should be around 160 ohm.
4.) The Switch should be NC by default.
5.) After the Skylight window is working, we can press the Red Button on the skylight controller for testing as it will be Open. Once we release the button, the Skylight Window will be closed.
The Cable at the Skylight Controller Output is not connected properly and is loosen causes there are no signal send to the Magnetic Controller.
Connect the Cable properly and tightly.
Check if the Skylight Window is working by pressing the RED BUTTON from the Skylight Controller on the Right side. After pressing the RED BUTTON, it will open automatically.