To have a better experience, please upgrade your IE browser.upgrade
Questo sito utilizza cookie di profilazione (propri e di terze parti) per ottimizzare la tua esperienza online e per inviarti pubblicità in linea con le tue preferenze. Continuando a utilizzare questo sito senza modificare le tue preferenze acconsenti all’uso dei cookie. Se vuoi saperne di più o negare il consenso a tutti o ad alcuni cookie clicca qui>
The website that you are visiting also provides Arabian language. Do you wish to switch language version?
يوفر موقع الويب الذي تزوره المحتوى باللغة العربية أيضًا. هل ترغب في تبديل إصدار اللغة؟
The website that you are visiting also provides Russia language Do you wish to switch language version?
Данный сайт есть в английской версии. Желаете ли Вы перейти на английскую версию?
1. ECNS210 has many critical alarms indicates that it cannot connect to all the ENODEBs.
2. EMRS cannot connect and login.
3. EMDC cannot connect to the U1911. The SIP trunk between MDC and U1911 was down.
4. EOMC lost the connection with all the ENODEBs.
Many critical alarms about lost connection between ECNS210 and EOMC910 with ENODEBs.
alrm IDis: 14001, 33310
1. Check if we make any configuration before the problem raised. --- Didn’t make any configuration.
2. For the ECNS210 and EOMC cannot connect with the ENODEB, check the transition system. ----The RTN is active, but there is only small data transmit.
3. For the EMRS cannot connect, reboot the EMRS. After reboot the EMRS, it can connected.
4. For the EMDC cannot connect U1911, and the SIP trunk down, check the heartbeat configuration on the U1911 and EMDC, the heartbeat turned off. Reboot the U1911, there is nothing effective.
5. From above analyze we can know that the network must have some problem. We disconnect the cable connect to the customer switch to have a check.
6. After we disconnect the cable connect to the customer switch, all the problem above are solved, all the alarms disappeared.