To have a better experience, please upgrade your IE browser.upgrade
Questo sito utilizza cookie di profilazione (propri e di terze parti) per ottimizzare la tua esperienza online e per inviarti pubblicità in linea con le tue preferenze. Continuando a utilizzare questo sito senza modificare le tue preferenze acconsenti all’uso dei cookie. Se vuoi saperne di più o negare il consenso a tutti o ad alcuni cookie clicca qui>
The website that you are visiting also provides Arabian language. Do you wish to switch language version?
يوفر موقع الويب الذي تزوره المحتوى باللغة العربية أيضًا. هل ترغب في تبديل إصدار اللغة؟
The website that you are visiting also provides Russia language Do you wish to switch language version?
Данный сайт есть в английской версии. Желаете ли Вы перейти на английскую версию?
After communicate with FSE, the problem are Alarm ID 0358-001(UPS is working in Bypass mode) and Alarm ID 0193-001(mains three-phase current is imbalance) on UPS LCD.
1. For Alarm 0358-001, The UPS is working in Bypass mode from 2017.06.11.If the AC input is outage, the load will be shut down.
Ø Start the inverter. Let UPS transfer to invertor mode. When AC input is outage, the UPS will transfer to battery mode automatically.
2. For Alarm 0193-001,the mains three-phase current is imbalance.
Ø The current of Phase A and Phase B are 0 A. Only phase C is 9.7A. The AC output phase current is imbalance. And have confirmed with customer, they didn't connect load on phase A and phase B. So this alarm is normal.
Ø When UPS is working in invertor mode, it will not affect UPS working. if customer don't want to see this alarm. We can disable this alarm.
Customer didn't connect load on phase A and phase B. So load is imbalance in each phase.
Ø Start the inverter. Let UPS transfer to inverter mode. when AC input is outage, the UPS will transfer to battery mode automaticallyØ If customer have many loads, it is better to let each phase loads balance.
Ø If customer only has little load. and don’t want to see this alarm. Please Disable the Min. main input cur.exceed option.
Step 1. Click system Info
Step 2 Click setting
Step 3 Input user name and password. Default user name: admin. Default password: 000001
Step 4 Click PDU Param. to set related parameters
Step 5 Find Min. main input cur.exceed option, and disable this option.
Note: If the version of UPS5000 is V100R002C41SPC100. We need to set Min. main input cur.exceed to disable this alarm. But if it is V100R002C41SPC300, We need to set Min. input 3-phase cur.imb to disable