Questo sito utilizza cookie di profilazione (propri e di terze parti) per ottimizzare la tua esperienza online e per inviarti pubblicità in linea con le tue preferenze. Continuando a utilizzare questo sito senza modificare le tue preferenze acconsenti all’uso dei cookie. Se vuoi saperne di più o negare il consenso a tutti o ad alcuni cookie clicca qui>
The website that you are visiting also provides Arabian language. Do you wish to switch language version?
يوفر موقع الويب الذي تزوره المحتوى باللغة العربية أيضًا. هل ترغب في تبديل إصدار اللغة؟
The website that you are visiting also provides Russia language Do you wish to switch language version?
Данный сайт есть в английской версии. Желаете ли Вы перейти на английскую версию?
In project O of country C, batteries cannot be installed according to the layout because the power room area is insufficient.
The power room layout shows that the six battery strings should be installed in parallel. In fact, the batteries cannot be installed according to the layout because the power room area is insufficient.
The power room is small. The entire power system consists of one Emerson PS481000-2/100 (including an AC power cabinet, two DC power cabinets, two rectifier cabinets, and four external 2000 Ah battery strings), two NXa40KVA uninterruptible power supplies (UPSs), and two dedicated battery strings. The survey personnel did not understand the power equipment size, so the batteries cannot be installed.
Install UPS batteries vertically and install two power batteries according to the layout. Prepare a support based on the battery rack dimensions and stack the other two battery strings on the battery rack. Secure the support and ensure that the support can bear the battery weight. Before starting the handling process, reach an agreement with the customer.