To calculate the gauge thickness of power cable between the source and the equipmnet.
This is required to decide on the thickness of the power cable to be laid between the dcdb and our router.
The relevant documents were searched and the calculation formula explained to the customer after which the matter was solved.
During the ATP customer insisted from us for the justification of the power cable gauge we had laid up to our routers.it was calculated as per the foloowing;
S= ∑ i x L
?U x K
S =Cross Sectional area
K=Constant, 57 for copper & 34 for Aluminum
Please refer to the attached document for power cable gauge calculation.