Customer from XXX country raise an issue regarding Comp Suction LP lock alarm on ECC800 in FusionModule 800.
Comp Suction LP lock alarm, a060
1) As per conversation with customer, this is a new delivery. Requested customer to import logs from ECC800
1) From the logs collected, we can see that the suction preseure on the NetCol 5000 is lower that usual, the range must be from 0.7MPa-1.2MPA. In the logs we can see that the suction pressure drops to 0.11MPa
( Suction Pressure logs can be obtained under run_log.csv)